The performance of the automatic temperature control system of the reactor is very important. Once you encounter a failure that cannot be started, you must solve it as soon as possible, otherwise the uncontrollable temperature will affect the reaction materials.
If you encounter a compressor startup failure in the automatic temperature control system of the reactor, first check whether the power supply is normal. The power supply voltage should not exceed or be lower than the rated voltage of the unit. Commonly used voltages are 3-phase 380V and single-phase 220V. When the voltage is too low or too high, the automatic temperature control system of the reactor cannot be started. For compressor units with a water system, carefully check whether there is water in the cooling water system and the chilled water system, whether the water pressure is normal, and whether the cooling water and chilled water pipeline systems are unblocked.
Check whether the various pressure gauges, thermometers, flow meters, solenoid valves, relays, and energy regulating valves of the automatic temperature control system of the industrial reactor are in good condition. Check the transmission device, if it is driven by a belt, whether its various protective devices are completely reliable, and whether all kinds of wrong equipment and protective equipment are complete and effective. Check whether the various valves of the high-pressure system and low-pressure system of the industrial reactor automatic temperature control system are in the correct switching state when starting or running.
Check the crankcase lubricant. The oil level should not be lower than or higher than the indicated oil level. If the lubricating oil is insufficient, add enough lubricating oil of the same specification and model. Check whether the refrigerant system of the automatic temperature control system of the industrial reactor is leaking, and whether the lubricating oil system is leaking. Check whether the liquid level of the liquid storage tank is normal, and the liquid level should be kept between one-third and two-thirds.
Next, follow the steps to troubleshoot, first check the main circuit. For example, whether the power supply has electricity, whether the voltage is normal, whether the fuse has been blown due to starting overload, whether the air switch is tripped, whether the switch contacts are good, and whether the power supply lacks phase.
Observe the voltmeter and ammeter when starting. When the automatic temperature control system of the reactor is not equipped with an ammeter or voltmeter, a multimeter or a tester can be used to check the power supply. When the power supply voltage is too low, the compressor cannot be started. For piston refrigeration compressors, whether the large-end bearing bushes and the curved sleeves of the connecting rods hold shafts. These can be caused by the excessively high exhaust temperature during the previous operation, or it can be caused by the coking of the lubricating oil, which makes the cylinder and the piston stick together, making the compressor unable to start. Check differential pressure relay and high and low voltage relay. When the oil pressure of the compressor is abnormal, the compressor can be stopped.
At the same time, when the compressor discharge pressure and suction pressure are abnormal, neither can start or the compressor will stop running soon after it has started. Check whether the amount of chilled water, cooling water, and water temperature are normal. If the water volume is small and the water temperature is high, it will cause the condensing pressure to rise sharply and the evaporation temperature to drop rapidly. Due to the action of the unit protection facilities, the unit often shuts down quickly. Check whether the relevant solenoid valves and regulating valves are out of order, and whether they are opened or closed as required. Check whether there is a leakage of working fluid in the temperature sensing bag of the temperature relay, or the adjustment is wrong.
Hot water circulation, this is a very good water heater device and is now used in many places. By using a hot water circulator, people can solve the problem of domestic hot water use. Today we will introduce some applications of hot water ...View Details
How to judge the operating status of the chemical and pharmaceutical constant temperature control sy160
Nowadays, many pharmaceutical and chemical industries use LNEYA's constant temperature control system. How to judge its operation status during operation?There should be no noise in the cylinder of the chemical and pharmaceutical thermosta...View Details
1. Generally speaking, the design of general comfortable air-conditioning environment is simple (not constant temperature and humidity variable flow water system). The selection of water system flow, pump and pipe diameter is not a prob...View Details