What are the influences on the refrigeration factors of the enclosed explosion-proof chiller?
Check if it is the cause of the failure of the enclosed explosion-proof chiller. This selection must be accurate. If the model is not in place, the required cooling effect will not be achieved. It is recommended that the user will need it when purchasing the enclosed explosion-proof chiller. The cooling capacity and other parameters are provided to the chiller manufacturer, and professionals will select the model for you to achieve the required cooling effect.
The enclosed explosion-proof chiller has higher requirements for the working environment, because it is cooled by hot air circulation. If the ventilation effect of the installation workshop is not good, it will directly affect the cooling effect. There is more dust on the surface of the compressor, which leads to slow heat dissipation of the compressor and indirectly affects the cooling effect. There is leakage or shortage of refrigerant in the enclosed explosion-proof chiller, which leads to a decline in the cooling effect of the chiller. The accumulation of debris or sludge in the evaporator causes the flow rate to slow down, which affects the evaporation and condensation capacity and reduces the cooling effect.
The dust in the condenser of the enclosed explosion-proof chiller will affect the heat dissipation effect. The equipped unit is operating at full load, and the ambient temperature rises, resulting in insufficient cooling power and thus affecting the cooling effect.
Insufficient refrigerant, which is what we often call Freon, will also lead to poor cooling performance of the enclosed explosion-proof chiller. During the operation of the chiller, the liquid refrigerant in the evaporator continuously absorbs heat from the water and starts to evaporate. After the compressor is compressed and throttled by the expansion valve, it becomes a low-temperature and low-pressure refrigerant and enters the evaporator to continue. Circulation, if the use time is too long, the refrigerant will volatilize, which will affect the cooling effect.
When the filter of the enclosed explosion-proof chiller is blocked, it affects the heat exchange effect of the condenser, and the cooling effect of the whole machine is not good. It needs to be checked regularly and cleaned. When the filter is seriously clogged, it is recommended to replace the new filter drier.
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
July 4, 2018Guanya is a leading role in heating cooling circulator. It provides the customers with proposal and technology of controlling the cold and heat, temperature control system with stable property, extend...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
April 10, 2018Low Temperature Cooling Chiller LT model: LT-5018N，LT-5040N，LT-5062N，LT-5090N，LT-50A1N，LT-50A2N; Medium Temperature Range: -45℃～30℃. ASET multifunctional controller, control outlet temperature of water tankview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view