What to do if there is a failure and alarm
during the use of the recirculating chiller equipment? In order to ensure
production, such problems need to be resolved quickly.
We must first understand the causes of
failures and alarms, and adopt different solutions for different causes. Common
recirculation chiller equipment failures and alarms include reverse phase
alarm, contactor jam alarm, over-temperature protection alarm, abnormal
pressure alarm, overload alarm, etc. No matter what kind of fault alarm, it can
be known according to the alarm light and alarm signal information.
1. Recirculation chiller equipment reverse
When a reverse phase alarm occurs in the recirculation chiller
equipment, the circulating pump cannot be started. There are two reasons for
the reverse phase alarm of the high and low temperature cold water circulation
device. One is that the phase sequence of the three-phase power line is
connected incorrectly, and the other is that the reverse protector fails. If
the phase sequence of the three-phase power cord is connected incorrectly, just
adjust the phase sequence directly. If the reverse phase protector fails, it
needs to be replaced.
2. Contactor stuck alarm
Recirculation chiller equipment contactor
stuck alarm, the over-temperature indicator will also be on, generally there
are three reasons: one is the heating AC contactor stuck, the other is the
computer board heating has been outputting, there is a problem, and the third
is the over-temperature The protection switch operates incorrectly. When the
contactor is stuck and alarms, the continuous heating of the heat transfer oil
will cause danger, so deal with it in time.
3. Alarm for lack of media
In order to protect the heating pipe and circulating pump of the
recirculating chiller equipment, the system will stop heating when there is a
shortage of media. When there is a lack of media, check whether there is a lack
of media (water or oil). If the water temperature meter shows that there is a
lack of media, you can adjust the pressure value of the pressure switch to a
4. Overload alarm
When the recirculation chiller equipment has an overload alarm,
check whether the circulating pump is overloaded. If the pump is overloaded,
you can increase the overload current ampere.
When the recirculation chiller equipment
fails and alarms, as long as it is dealt with in time, there will be no safety
issues. LNEYA is a manufacturer of recirculating chiller equipment, equipped
with an after-sales service system. For minor problems such as fault alarms,
you can consult us email@example.com for a faster and safer solution.
The production process of traditional Chinese medicine raw materials is relatively complicated: long process, many pipelines, and complicated operations; and most of the preparation raw materials are unstable, such as high environmental pa...View Details
As technology continues to advance and improve, LNEYA recommends strict requirements for operators of large thermal shock test chambers. If used improperly, operators need to be able to face and resolve these problems in a timely manner. ...View Details
LNEYA closed cycle refrigerators should start to pay attention to their maintenance work after a long time of use, then how to carry out maintenance work? How to do maintenance work for it? According to the specific use environment and th...View Details
Industrial chillers are composed of compressors, condensers, evaporators, expansion valves and other accessories.1. Compressor: In the industrial chiller system, the compressor is the power to ensure refrigeration. The compressor is used t...View Details