Industrial chiller is also known as industrial water cooled chiller, screw chiller, fluid cooler, produced by Wuxi LNEYA chiller Company as professional industrial chiller manufacturer and supplier of cold water machine, deep refrigeration industry, with its high-quality customer service and cost-effective chiller refrigeration technology and price, exquisite customer services. The chiller consists of four main components: compressor, evaporator, condenser and expansion valve, thus the effect of cooling and heating of the unit is realized.
With the continuous development of the times, industrial chillers are constantly improving. Of course, we have a lot of space in the selection as an expert industrial chiller manufacturer. Today Lneya chiller shares with everyone the oil circulation measurement method for industrial chillers.
First: weighing method
The oil circulator of the current refrigeration compressor adopts a weighing method in many cases. That is, the amount of oil in the condenser is weighed and measured in batches. When using this method, it is necessary to measure the working conditions according to the refrigerant compressor' standard to run to a stable state.
Second: Oil separation
The oil separator is used for separation. In operation, an oil separator is installed on the side of the chiller compressor exhaust pipe. As a result, the compressor exhausts the oil in the mixture through the oil separator. Separated and collected into the container, the size of the oil circulation rate can be calculated based on the change and the amount of refrigerant circulating. This method can see the change of oil circulation rate at different times.
Third: Optical Testing
There are two methods for optical testing. The first one is a power-off sensor that uses the amount of gas refrigerant contained in the exhaust pipe of a chiller compressor as the target and measures the attenuation of cold oil produced by a broadband sensor so that it can be tested the amount of oil contained in the gas.