Transmission powertrain cooling system with evaporator
The evaporator is one of the four major components of the refrigeration system, and it is the ultimate embodiment of the refrigeration effect and efficiency. The evaporator is generally designed and equipped by the transmission powertrain cooling system manufacturer, and the user does not need to choose. However, in order to better maintain the refrigeration system and ensure its operation, the following points should be noted:
1. The influence of liquid level on evaporation temperature. Due to the height of the refrigerant liquid column, the evaporation temperature at the bottom of the flooded evaporator is higher than the evaporation temperature of the liquid surface. The evaporation temperature of different refrigerants at different liquid levels is affected differently by the height of the static liquid. Regardless of the refrigerant, the lower the evaporation temperature of the liquid surface, the greater the influence of the hydrostatic height on the evaporation temperature. Therefore, only when the evaporation pressure is high, the influence of the hydrostatic height on the evaporation temperature can be ignored. When the evaporation temperature is low, it cannot be ignored. In other words, it becomes uneconomical to use a flooded evaporator at this time.
2. The possibility of freezing of the refrigerant. If the evaporation temperature is lower than the freezing temperature of the refrigerant, the refrigerant may freeze. When water is used as the refrigerant, theoretically, the temperature of the inner wall of the tube can be as low as possible. However, for the sake of simplicity, the temperature of the inner wall of the pipe at the outlet end of the latter process is usually kept above. For the case of brine as the refrigerant, according to the same principle, the temperature of the inner wall of the tube should be higher than the freezing temperature of the refrigerant.
3. The pressure loss of the refrigerant in the evaporator. When the refrigerant flows through the evaporator, pressure loss is caused, which will inevitably make the pressure p2 of the refrigerant at the outlet of the evaporator be lower than the pressure p1 at the inlet, thereby reducing the suction pressure of the compressor, resulting in a decline in the refrigeration capacity.
4. According to different models, the choice of evaporator is different. For example, the cooling system of the box-type small transmission powertrain uses a water tank coil type evaporator; the open type small transmission powertrain cooling system and the small screw type For transmission powertrain cooling system, shell and tube evaporator is used; for acid and alkali resistant transmission powertrain cooling system, titanium tube evaporator or stainless steel plate exchanger can be selected.
There are many options for the cooling system of the small transmission powertrain. Of course, it can be customized according to the needs of users.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
December 5, 2022On November 18, 2022, it was sponsored by the Jiangsu Provincial Association for Science and Technology, the Provincial Taiwan Affairs Office, the Provincial Department of Industry and Information Tec...view
January 13, 2023Recently, the Jiangsu Provincial Productivity Promotion Center officially released the evaluation results of the unicorn enterprises and gazelle enterprises in 2022 in Jiangsu and the high-tech zone, ...view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view