How to reduce the condensing pressure of the heating circulator unit?
During the operation of the heating circulator unit, the temperature change inside the equipment will cause the condensing pressure to change. Especially in summer when the condensing pressure is too high, the power consumption of the compressor will continue to increase, resulting in a gradual decrease in the cooling capacity, which indirectly makes the equipment cycle worse. It is necessary to appropriately reduce the condensing pressure.
1. Then, when the condensing pressure of the heating circulator unit is too low, the power supply of the throttle valve is insufficient, and the high-pressure liquid pipe is continuously affected by the heating factor, which will reduce the capacity of the throttle valve.
2. The pressure of the condenser can be controlled by adjusting the heat exchange capacity of the condenser. When the heat exchange of the condenser is large, the gas discharged from the compressor is fully condensed, and the condensing pressure gradually decreases; if the heat exchange performance of the condenser is weakened, the condensing pressure continues to rise.
3. The condenser can adjust the cooling water flow to control the condensation pressure. Install a regulating valve on the condenser cooling water outlet pipe. There are two modes for the water volume control valve: one is a temperature type water volume control valve that uses the temperature at the outlet of the cooling water of the condenser to indirectly send a letter. It has a temperature sensor that is inserted into the condensate outlet. When the water temperature rises, the valve opens large; when the water temperature decreases, the valve closes small. The other is a pressure-type water volume regulating valve that directly sends a signal from the condensing pressure, and the pressure signal is drawn from the condenser. When the condensing pressure gradually increases, the valve opens large; when the condensing pressure decreases, the valve closes small, thereby changing the cooling water flow of the condenser.
4. The self-contained cooling tower circulation system can be used. In order to prevent the condensation pressure from being too low, it can be adjusted by the water bypass valve, which makes part of the water from the condenser sent to the cooling tower for cooling, and the other part is returned to the bypass. water outlet.
For the LNEYA heating circulator unit, if multiple pumps are used in parallel, the number of running pumps can be changed to adjust the flow rate according to the constant change of the condensing pressure.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
December 5, 2022On November 18, 2022, it was sponsored by the Jiangsu Provincial Association for Science and Technology, the Provincial Taiwan Affairs Office, the Provincial Department of Industry and Information Tec...view
January 13, 2023Recently, the Jiangsu Provincial Productivity Promotion Center officially released the evaluation results of the unicorn enterprises and gazelle enterprises in 2022 in Jiangsu and the high-tech zone, ...view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view