What to do if there is a failure and alarm during the use of the recirculating chiller equipment? In order to ensure production, such problems need to be resolved quickly.
We must first understand the causes of failures and alarms, and adopt different solutions for different causes. Common recirculation chiller equipment failures and alarms include reverse phase alarm, contactor jam alarm, over-temperature protection alarm, abnormal pressure alarm, overload alarm, etc. No matter what kind of fault alarm, it can be known according to the alarm light and alarm signal information.
1. Recirculation chiller equipment reverse phase alarm
When a reverse phase alarm occurs in the recirculation chiller equipment, the circulating pump cannot be started. There are two reasons for the reverse phase alarm of the high and low temperature cold water circulation device. One is that the phase sequence of the three-phase power line is connected incorrectly, and the other is that the reverse protector fails. If the phase sequence of the three-phase power cord is connected incorrectly, just adjust the phase sequence directly. If the reverse phase protector fails, it needs to be replaced.
2. Contactor stuck alarm
Recirculation chiller equipment contactor stuck alarm, the over-temperature indicator will also be on, generally there are three reasons: one is the heating AC contactor stuck, the other is the computer board heating has been outputting, there is a problem, and the third is the over-temperature The protection switch operates incorrectly. When the contactor is stuck and alarms, the continuous heating of the heat transfer oil will cause danger, so deal with it in time.
3. Alarm for lack of media
In order to protect the heating pipe and circulating pump of the recirculating chiller equipment, the system will stop heating when there is a shortage of media. When there is a lack of media, check whether there is a lack of media (water or oil). If the water temperature meter shows that there is a lack of media, you can adjust the pressure value of the pressure switch to a lower value.
4. Overload alarm
When the recirculation chiller equipment has an overload alarm, check whether the circulating pump is overloaded. If the pump is overloaded, you can increase the overload current ampere.
When the recirculation chiller equipment fails and alarms, as long as it is dealt with in time, there will be no safety issues. LNEYA is a manufacturer of recirculating chiller equipment, equipped with an after-sales service system. For minor problems such as fault alarms, you can consult us email@example.com for a faster and safer solution.
The high-precision high-low temperature circulator is one of the equipments used in the pharmaceutical and chemical industry to support various reactors. If users encounter an abnormal power outage during use, they should pay attention to ...View Details
In the experimental equipment, the walk-in lab water chiller is used for all kinds of electronic components in high and low temperature or hot and wet environment to test the requirements of various performance indicators. It is generally ...View Details
In the chemical laboratory, pilot plant and reaction process, temperature control requires the use of dynamic temperature control systems. When controlling the reactor, the exothermic and endothermic reactions must be compensated with high...View Details