How to deal with the equipment failure alarm of the recirculating chiller
What to do if there is a failure and alarm during the use of the recirculating chiller equipment? In order to ensure production, such problems need to be resolved quickly.
We must first understand the causes of failures and alarms, and adopt different solutions for different causes. Common recirculation chiller equipment failures and alarms include reverse phase alarm, contactor jam alarm, over-temperature protection alarm, abnormal pressure alarm, overload alarm, etc. No matter what kind of fault alarm, it can be known according to the alarm light and alarm signal information.
1. Recirculation chiller equipment reverse phase alarm When a reverse phase alarm occurs in the recirculation chiller equipment, the circulating pump cannot be started. There are two reasons for the reverse phase alarm of the high and low temperature cold water circulation device. One is that the phase sequence of the three-phase power line is connected incorrectly, and the other is that the reverse protector fails. If the phase sequence of the three-phase power cord is connected incorrectly, just adjust the phase sequence directly. If the reverse phase protector fails, it needs to be replaced.
2. Contactor stuck alarm Recirculation chiller equipment contactor stuck alarm, the over-temperature indicator will also be on, generally there are three reasons: one is the heating AC contactor stuck, the other is the computer board heating has been outputting, there is a problem, and the third is the over-temperature The protection switch operates incorrectly. When the contactor is stuck and alarms, the continuous heating of the heat transfer oil will cause danger, so deal with it in time.
3. Alarm for lack of media In order to protect the heating pipe and circulating pump of the recirculating chiller equipment, the system will stop heating when there is a shortage of media. When there is a lack of media, check whether there is a lack of media (water or oil). If the water temperature meter shows that there is a lack of media, you can adjust the pressure value of the pressure switch to a lower value.
4. Overload alarm When the recirculation chiller equipment has an overload alarm, check whether the circulating pump is overloaded. If the pump is overloaded, you can increase the overload current ampere.
When the recirculation chiller equipment fails and alarms, as long as it is dealt with in time, there will be no safety issues. LNEYA is a manufacturer of recirculating chiller equipment, equipped with an after-sales service system. For minor problems such as fault alarms, you can consult us email@example.com for a faster and safer solution.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
April 10, 2018Low Temperature Cooling Chiller LT model: LT-5018N，LT-5040N，LT-5062N，LT-5090N，LT-50A1N，LT-50A2N; Medium Temperature Range: -45℃～30℃. ASET multifunctional controller, control outlet temperature of water tankview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view