How to judge the operating status of the chemical and pharmaceutical constant temperature control sy
Nowadays, many pharmaceutical and chemical industries use LNEYA's constant temperature control system. How to judge its operation status during operation?
There should be no noise in the cylinder of the chemical and pharmaceutical thermostatic control system, only the normal and regular sound of the inhalation valve. The condenser cooling water should be sufficient, the water pressure should be above 0.12MPA, and the water temperature should not be too high. There should be no foot heating and frosting on the cylinder wall, and the surface temperature difference should not exceed 15-20 degrees. For refrigerated or low-temperature systems, frosting on the suction pipe can generally reach the suction port; for high-temperature conditions, the suction pipe should not be condensed Frost, condensation is normal.
Chemical and pharmaceutical constant temperature control system Crankcase oil temperature small constant temperature control system does not exceed 70 degrees and not less than 10 degrees. The lubricating oil may have foam, and the exhaust temperature should not be too high. Too high and close to the flash point of domestic refrigeration oil will be detrimental to the equipment. The condensing pressure is not easy to be too high, and the construction capacity of the condensing pressure cold storage is affected by the water source, condensing method and refrigerant. The oil level of the crankcase shall not be lower than 1/2 of the horizontal centerline of the sight glass.
Chemical and pharmaceutical thermostatic control system. The hand-touched horizontal accumulator and oil separator should be cool in the upper part and lower part, and the liquid or oil level at the junction of cold and hot. The safety valve or bypass valve should be cool at the low pressure end, otherwise the high and low pressure series gas. During operation, the evaporating pressure and the suction pressure should be similar, and the exhaust pressure and condensing pressure should be similar to the accumulator pressure.
There should be a temperature difference between the cooling water in and out of the chemical and pharmaceutical constant temperature control system. If there is no or very slight temperature difference, it means that the heat exchanger is dirty and needs to be cleaned. The system should be sealed, and no refrigerant or lubricating oil should be leaked. The shaft seal of the fluorine small constant temperature control system should not drip oil. The temperature of the shaft seal and bearing of the constant temperature control system for chemical and pharmaceutical industries does not exceed 70 degrees. The valve body of the expansion valve is evenly frosted or condensed, but there should be no thick frosting at the inlet. When the fluid passes through the expansion valve, only a dull, small sound can be heard. The pointers of the pressure gauges in the system should be relatively stable and the temperature indication should be correct.
The above conditions related to the chemical and pharmaceutical thermostatic control system can be used to judge the operation status. It is recommended that the operator observe more to determine the faulty sound in time and solve it effectively.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
December 5, 2022On November 18, 2022, it was sponsored by the Jiangsu Provincial Association for Science and Technology, the Provincial Taiwan Affairs Office, the Provincial Department of Industry and Information Tec...view
January 13, 2023Recently, the Jiangsu Provincial Productivity Promotion Center officially released the evaluation results of the unicorn enterprises and gazelle enterprises in 2022 in Jiangsu and the high-tech zone, ...view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view