The 500 liter reactor chiller is used more in the pharmaceutical industry. Therefore, the user needs to select a regular manufacturer when selecting, and at the same time, understand the features and configuration.
For the selection of 500 liter reactor chiller, comprehensive technical and economic comparison should be made according to working conditions, cooling capacity, local power source, water source, heat source, gas source and other factors through investment, operation cost, energy consumption and environmental protection. Then determine the budget.
In areas with abundant power supply, the 500-liter reactor chiller unit with limited power should be selected. Generally, in the case of Q0>1163kw, the centrifugal 500 liter reactor chiller group is generally used; when Q0=582～1163kw, it is generally adopted. The screw type 500 liter reactor chiller group or the centrifugal type 500 liter reactor chiller group; when Q0 < 582 kW, the piston type 500 liter reactor chiller group is generally used.
Generally, the energy efficiency ratio of an electric-powered refrigerator is higher than that of an absorption-type 500-liter reactor cooler group. The order of energy consumption per unit cooling capacity is generally: centrifugal, screw, piston, and absorption ( Direct combustion type, steam type, hot water type). For places with residual heat or waste heat utilization and places where electricity is lacking, the absorption type 500 liter reactor cooler group should be preferred.
Wuxi Guanya (LNEYA) 500 liter reactor chiller adopts fully enclosed circulation pipeline, compact structure, single-machine self-cascading refrigeration technology, and brand accessory configuration to achieve rapid cooling.