The water pump is one of the important auxiliary components of the refrigeration system of the industrial water chiller. Many industries will use the industrial water chiller, but many people don’t know much about the equipment. This time, lneya refrigeration will talk about the role of the water pump of the industrial water chiller.
The function of the water pump of the industrial water chiller is to provide pressure and water flow according to the needs of the system. The chilled water pump is the water pump, also known as the circulating water pump. Of course, the chilled water pump is not only the water pump in the industrial water chiller system, but also may exist in the cooling water system of the air-cooled water chiller.
The water pump of industrial water chiller can determine the water flow of chilled water, that is, the water flow of chilled water is not only affected by the size and capacity of the water tank, but also affected by the chilled water pump. The water flow can determine the range of refrigeration temperature to some extent. When the same cooling capacity is transmitted with chilled water as refrigerant, the larger the water flow is, the higher the temperature of the cooling capacity will be.
Water flow is controlled by chilled water pump, so there is a close relationship between chilled water pump and industrial water chiller refrigeration. The specific reasons are as follows: while the water flow of the industrial water chiller increases, the cooling capacity of the chilled water per unit area will decrease. Although the total cooling capacity remains unchanged, the cooling capacity per unit area of the chilled water has decreased. Therefore, if the chilled water flow is large, the cooling effect will become worse and the temperature will become higher, However, this does not mean that the refrigeration capacity of the compressor and the whole chiller system becomes worse.
The chilled water system includes water pipeline, chilled water tank, water pump, etc. the specific parameter selection and xing’shi selection of the water pump are closely related to the model of the industrial chiller. Whether the type of the water pump and the parameter model can be selected will directly determine the refrigeration capacity of the industrial chiller and even whether the industrial chiller can work normally.
About the role of industrial water chiller water pump, that’s it. If you don’t understand, please consult us!
Selection and installation of the expansion valve for ultra low temperature recirculating chillers: the selection of expansion valve plays an important role in the performance of the ultra low temperature recirculating chiller refrigeratio...View Details
How to use the 4kW new energy charging pile cooling system? The 4kW new energy charging pile cooling system is able to provide high and low temperature environments and is widely used in many fields such as material science, new ener...View Details
The minus 30 degree ethylene glycol chiller is a single-fluid low-temperature refrigeration unit with compressor refrigeration. How should the user set it better when operating it? 1. Automatic logout timeAutomatic logout means that...View Details
The semiconductor cooling cycle system is a device for cooling the semiconductor heating part. LushiA reminds that if the cooling capacity is insufficient during the operation, it is necessary to check in time to see if something has gone ...View Details