What are the effects of oil level and oil difference in low temperature chillers?
LNEYA tells you that in addition to the refrigeration system, the lubricating oil system is also an important part, with its own oil storage and special oil cooler.
It refers to the level of the lubricant in the oil storage container. The oil storage container of the low temperature chiller is provided with an oil level display device. Generally, the oil level in the oil storage container should be 5 mm below the central horizontal line of the mirror. The purpose of specifying the height of the oil level is to ensure that the amount of oil required to form an oil circuit is sufficient when the pump is in operation. If the oil level is too low, it may cause the pump to be insufficient, causing malfunction or damage to the equipment.
Oil pressure difference
It is the guarantee that the lubricating oil is driven by the oil pump to flow to the working parts in the oil system pipeline to overcome the flow resistance. Without sufficient oil pressure difference, there is no guarantee that the lubricating system of the cold and low temperature chiller has sufficient lubrication and cooling oil and the power required to drive the energy regulating device. Therefore, the low temperature chiller manufacturer reminds that the oil pressure difference of the oil system It must be ensured within a reasonable range so that the moving parts of the unit can be fully lubricated and cooled, and the energy adjustment device can be flexibly operated.
Oil temperature refers to the temperature of the lubricating oil when the low temperature chiller is working. The temperature of the oil will have an important effect on the viscosity of the lubricant. If the oil temperature is too low, the viscosity of the oil increases, the fluidity decreases, and a uniform oil film is not easily formed, so that the desired lubrication effect cannot be achieved, and the flow speed of the oil is lowered, the lubrication amount is reduced, and the power consumption of the oil pump is reduced. Increase; oil temperature is too high, the viscosity of the oil will drop, the oil film will not reach a certain thickness, so that the running parts are difficult to withstand the necessary working pressure, resulting in deterioration of the lubrication condition, causing the wear of the moving parts to intensify, causing the chiller to malfunction.
Through the above explanation, I believe that everyone understands the impact of oil level and oil difference. In order to better use the low temperature chiller, we still need to know carefully about these operating points!
- July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
- July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
- July 4, 2018Guanya is a leading role in heating cooling circulator. It provides the customers with proposal and technology of controlling the cold and heat, temperature control system with stable property, extend...view
- July 4, 2018The price of heating cooling circulator is determined by raw materials, manufacturing overhead, technical cost, impacting on the final quotation.The heating cooling circulator is made of shell and int...view
- July 4, 2018With the continuous development of enterprises, as a matching equipment used in the lad, the heating cooling circulator which acts as a brand for manufacturers will be prosperous in the market, accele...view
- July 4, 2018The refrigeration principle of the so-called low temperature chiller is to use the artificial method, compressor refrigeration, through energy consumption, in a cycle process, in the process that cool...view
- January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
- March 30, 2018Performance characteristics：1. In the refrigeration system, the condensation adopts air cooling mode, which has a wide temperature control range, which can meet the user's various needs.2. With a unique b...view
- April 8, 2018Performance characteristics: 1. With wide temperature control range, can meet the user's various needs.2. With a unique balanced temperature control method, with stable and balanced heating capacity, high precision and high stable temperature control canview
- April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
- April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
- April 10, 2018ModelHQ-0540HQ-1040HQ-2540HQ-5040HQ-0575WHQ-1075WHQ-2575WHQ-5075WGas flow5m3/h10m3/h25m3/h50m3/h5m3/h10m3/h25m3/h50m3/hLowest Temp.-40℃-40℃-40℃-40℃-75℃-75℃-75℃-75℃Primary Temp.There is no-20℃...view