What are the effects of oil level and oil difference in low temperature chillers?
LNEYA tells you that in addition to the refrigeration system, the lubricating oil system is also an important part, with its own oil storage and special oil cooler.
It refers to the level of the lubricant in the oil storage container. The oil storage container of the low temperature chiller is provided with an oil level display device. Generally, the oil level in the oil storage container should be 5 mm below the central horizontal line of the mirror. The purpose of specifying the height of the oil level is to ensure that the amount of oil required to form an oil circuit is sufficient when the pump is in operation. If the oil level is too low, it may cause the pump to be insufficient, causing malfunction or damage to the equipment.
Oil pressure difference
It is the guarantee that the lubricating oil is driven by the oil pump to flow to the working parts in the oil system pipeline to overcome the flow resistance. Without sufficient oil pressure difference, there is no guarantee that the lubricating system of the cold and low temperature chiller has sufficient lubrication and cooling oil and the power required to drive the energy regulating device. Therefore, the low temperature chiller manufacturer reminds that the oil pressure difference of the oil system It must be ensured within a reasonable range so that the moving parts of the unit can be fully lubricated and cooled, and the energy adjustment device can be flexibly operated.
Oil temperature refers to the temperature of the lubricating oil when the low temperature chiller is working. The temperature of the oil will have an important effect on the viscosity of the lubricant. If the oil temperature is too low, the viscosity of the oil increases, the fluidity decreases, and a uniform oil film is not easily formed, so that the desired lubrication effect cannot be achieved, and the flow speed of the oil is lowered, the lubrication amount is reduced, and the power consumption of the oil pump is reduced. Increase; oil temperature is too high, the viscosity of the oil will drop, the oil film will not reach a certain thickness, so that the running parts are difficult to withstand the necessary working pressure, resulting in deterioration of the lubrication condition, causing the wear of the moving parts to intensify, causing the chiller to malfunction.
Through the above explanation, I believe that everyone understands the impact of oil level and oil difference. In order to better use the low temperature chiller, we still need to know carefully about these operating points!
- December 17, 2020December 16-18
Booth number: W5P08
Shanghai New International Expo Center (Pudong)view
- February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
- January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
- July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
- July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
- December 17, 2020LNEYA On November 3-5, meet at Chongqing International Expo Center [CIPM] Booth S3-07-2view
- January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
- April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
- April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
- April 10, 2018Low Temperature Cooling Chiller LT model: LT-5018N，LT-5040N，LT-5062N，LT-5090N，LT-50A1N，LT-50A2N; Medium Temperature Range: -45℃～30℃. ASET multifunctional controller, control outlet temperature of water tankview
- February 28, 2019-45℃~+200℃
- February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view