Troubleshooting of Common Faults of Industrial Water Chiller
As we all know, with the rapid development of modern industrial technology, in order to improve production efficiency, improve product quality and reduce consumption costs, the demand for temperature control equipment in the process is higher and higher, but there are more and more product quality problems about some industrial water chillers, So we simply analyze some common problems about industrial water chillers.
Abnormal temperature at the inlet and outlet of cooling water: the water temperature at the inlet of condenser is too high (higher than 32 ℃), first check whether the fan of cooling tower can be reversed (there are such examples in practical engineering). Then, after technical demonstration and on the premise of feasibility, adjust the blade angle of the fan to improve the air volume of the fan.
Another phenomenon often occurs in the system with multiple cooling towers in parallel. When the local load is running, the temperature difference between the inlet and outlet of the condenser is too small. It is necessary to check whether each cooling tower has been equipped with an electric valve, or whether the set electric valve fails to form a cooling water bypass, which can not be cooled completely.
The differential pressure at the inlet and outlet of cooling water is abnormal. According to the relevant refrigeration theory, the heat release of the condenser will directly affect the refrigeration capacity. Therefore, the user should first check the cooling water system based on the pressure loss value on the main engine. If the pressure difference obtained from the value of the pressure gauge at the inlet and outlet greatly exceeds the normal value, it indicates that there are sundries at the inlet of the condenser.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view