What are the noise reduction methods for industrial chillers?
Question: What are the noise reduction methods for industrial chilled water machines?
Answer: 1. Industrial industrial chilled water machine axial fan has different noise due to different wings and speed. The noise of octopole electromechanical is lower than that of hexapole electromechanical. The design should be selected flexibly according to the surrounding conditions and noise conditions, and strive to be economical and suitable.
2. In the design and equipment of industrial chillers, the noise is also different due to the different assembly methods of different models. The noise of hermetic compressors is lower than that of semi-hermetic compressors, and the noise of screw compressors is lower than that of piston compressors; the noise of several small refrigeration compressors is lower than that of a single refrigeration compressor.
3. When the industrial chiller is running, the vibration and noise of the refrigeration system and various settings have a greater impact on the surrounding conditions, and the ground feels vibrating. The working boundary of the electric fan of an industrial refrigerator is between 60 dB and 70 dB, so people cannot achieve normal work and rest in an emergency.
4. The best noise prevention operation steps for industrial chillers: industrial chillers, cooling water pumps, chilled water pumps, and system pipes should be isolated from vibration; refrigerators should be placed in the machine room or workshop with sound absorption and sound insulation, and should be placed in a place with smooth exhaust. Prevent the discharge from flowing back.
First of all, when choosing a chiller, choose a low-noise unit. The number of heat pumps in the chiller has a great influence on noise. The greater the number of heat pumps, the greater the noise, which must be considered comprehensively when using them.
The noise reduction of industrial chillers mainly considers the vibration and noise of the unit and pipeline. The usual solution is to install vibration damping equipment at the bottom of the chiller, and use spring hangers or brackets in the water pipe to reduce the vibration of the pipe. Vibration reduction measures should be taken to prevent the vibration of the chiller and water pump from spreading through the pipeline.
Compressor noise is included in the noise of the chiller. The noise of hermetic compressors is lower than that of semi-hermetic compressors. The noise reduction design should be based on the surrounding conditions, the unity of the effect and the cost. Air-cooled units and water pumps should be subjected to vibration reduction treatment, and sound barriers should be designed around the air-cooled units.
The cooler should be installed on the roof to prevent the noise of the cooler from affecting the building and its surrounding environment. For the chiller, the damper has good damping effect and wide frequency, which can effectively reduce the noise of the chiller.
When the industrial chiller is installed, the installation environment and location will cause noise problems. If the industrial refrigerator is in a relatively closed environment, the noise will be "amplified". The cramped environment will make the normal operation of industrial refrigerators louder than normal operation. It is recommended that both air-cooled and water-cooled refrigerators should be installed in a relatively open environment with no foreign objects around. If the requirements for environmental sound are high, a sound insulation wall can be installed and ventilation and heat dissipation can be maintained.
If the installation position of the industrial chiller is not leveled, it will cause the industrial chiller to move during normal operation. The vibration and shaking during normal operation will increase the amplitude of vibration and shaking under the condition of displacement, thereby generating a lot of noise.
Industrial chillers themselves, air coolers and water coolers are more prone to "noise" than the latter due to their different structures. As you know, air coolers use fans to dissipate heat from the condenser, while water coolers use a cooling tower system to dissipate heat from the condenser. Compared with the noise of the cooling tower (usually placed at a high place and not at the same position as the water cooler), the fan is noisier and is integrated with the main engine of the industrial chiller, making it easier to feel the presence of noise (cleaning and analyzing the blades or giving Lubricate the bearings).
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
April 10, 2018Low Temperature Cooling Chiller LT model: LT-5018N，LT-5040N，LT-5062N，LT-5090N，LT-50A1N，LT-50A2N; Medium Temperature Range: -45℃～30℃. ASET multifunctional controller, control outlet temperature of water tankview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view