Recirculating chillers are used frequently in the industry, and the heat generating parts of various devices require recirculating chillers, so operating efficiency is very important.
During the running time of the recirculating chiller, it is necessary to frequently check whether the cooling water pipe connection is safe and firm. Whether the flow, temperature and pressure of the cooling water are appropriate, so as not to affect the cooling effect of the recirculating chiller if the water flow is too large or too small.
The operator also needs to set a time to check the circulating water position of the water tank on a specific date each year to avoid the water level drop without knowing it, resulting in insufficient circulating water supply, so regular inspections and replenishment of circulating water.
During the use of the recirculating chiller, in order to prevent the growth of microorganisms and other substances in the circulating water and affect the cooling effect of the recirculating chiller, it is necessary to pay attention to water quality issues. It is recommended to check the water quality problems regularly and to replace the water quality at least annually.
In addition, the compressor air-cooled filter and the cooling fan blades in the recirculating chiller should be cleaned regularly. It is recommended that they should be cleaned every 6 months. After the cleaning is completed, 1 to 2 drops of oil should be added to the recirculating chiller fan bearing.
In order to reduce the impact of the scale of the recirculating chiller on the flow and cooling capacity, the pipeline is cleaned every 5 years (every 2 years if the tap water is used for cooling) to reduce the generation of pipeline scale.
As the weather temperature gradually increases, the use of liquid-cooled battery pack BMS test cooling water circulators also gradually reaches its peak. Liquid-cooled battery pack BMS test cooling water circulators have rated power rangin...View Details
LNEYA meets you again with CPIM The 56th (Fall 2018) National Pharmaceutical Machinery and China International Pharmaceutical Machinery Expo will be held from November 5th to November 7th, 2018 at Wuhan International Expo Center. ...View Details
The high and low temperature cooling circulator is developed and produced by LNEYA using its refrigeration and heating temperature control technology. When using high and low temperature cooling circulators, users are advised to use them a...View Details