As a industrial temperature control device, industrial water chiller is often in 24-hour operation. Therefore, it is very important to choose a industrial chiller with good performance. Wuxi Guanya Refrigeration Technology Co., Ltd. specializes in the manufacturing, research, development, production and sales of industrial temperature control equipment such as industrial water chiller and ultra-low temperature chiller. 15 years of concentration and experience have made LNEYA's industrial water chiller a leader in the industry. LNEYA specializes in providing customers with cooling and heating temperature control solutions, and meets customers’ temperature needs with superior performance industrial water chiller. In order to maximize the service life of the industrial water chiller, we need to know the following installation and maintenance methods in daily use.
Installation precautions: the installation site of the industrial water chiller must be the floor or installation mat, and can bear the operating weight of the chiller. It should be placed in a machine room with a room temperature of 4.4~43.3℃, and sufficient space shall be reserved around and above the industrial water chiller for daily maintenance. When the water source and the surrounding environment of the cooling water tower are bad, the cooling water circuit must be equipped with a Y-type filter and cleaned regularly. Choose the matching cooling tower according to the refrigeration capacity of the industrial water chiller. After the chilled water piping system passes the leak test, it is necessary to wrap the insulation layer to avoid cooling loss and dripping of the pipeline.
Maintenance method: If the industrial water chiller has been used for more than 6 months, and refrigeration capacity is reduced, please arrange staff to clean the radiator. If the industrial water chiller is equipped with a pressure gauge, check whether the pressure of the high pressure gauge is higher than 300PSI. If it exceeds, please clean the radiator or check whether the water hose has been fully opened. The repair is carried out according to the above operation for several times, but the alarm signal of industrial water chiller failure is still ringing, please arrange staff to repair it. After the chiller is out of service for a period of time, the water pump blade may be solidified due to the water dirt. When starting up again, the water pump rotor must be loosened first to avoid that the pump blade does not rotate and burn the motor.