What to do When the High Pressure Alarm of the Chiller？
People must pay attention to the maintenance of large-scale temperature control equipment such as industrial water chiller. Sometimes it is normal to encounter high-pressure alarm. We must first find out the causes of high-pressure of the industrial water chiller, and then we can solve the problem according to the remedy.
The causes of high pressure fault of industrial water chiller are as follows:
(1) The cooling water flow is insufficient to reach the rated water flow. The main performance is that the pressure difference between the inlet and outlet water of the unit becomes smaller (compared with the pressure difference at the beginning of system operation), and the temperature difference becomes larger. The reason for insufficient water flow is the lack of water or air in the system. The solution is to install an exhaust valve at the height of the pipeline for exhaust. If the pipeline filter is blocked and the water permeability is limited, appropriate filter shall be selected and the filter screen shall be cleaned regularly; The water pump is small and does not match the system.
(2) The cooling water temperature is too high and the condensation effect is not good. The rated working condition of cooling water required by the chiller is 30 ~ 35 ℃, high water temperature and poor heat dissipation effect will inevitably lead to high condensation pressure, which often occurs in high temperature season. The reason for high water temperature may be: cooling tower failure, such as the fan is not turned on or even reversed, and the water distributor does not turn, which shows that the cooling water temperature is very high and rises rapidly. The external temperature is high, the waterway is short and the amount of recyclable water is small. In this case, the cooling water temperature is generally maintained at a high level, which can be solved by increasing the water storage tank.
If you have seen the above two solutions and have other problems, you can contact us firstname.lastname@example.org 。 We lneya have professional technical engineers who can help you solve your questions.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
December 5, 2022On November 18, 2022, it was sponsored by the Jiangsu Provincial Association for Science and Technology, the Provincial Taiwan Affairs Office, the Provincial Department of Industry and Information Tec...view
January 13, 2023Recently, the Jiangsu Provincial Productivity Promotion Center officially released the evaluation results of the unicorn enterprises and gazelle enterprises in 2022 in Jiangsu and the high-tech zone, ...view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view