What is the reason for non condensable gas in the condenser of ultra-low temperature cooling water c
When the ultra-low temperature cooling water chiller is running, it is necessary to pay attention to the gas state generated by the condenser under a certain temperature and pressure. The existence of these gases affects the operation of the ultra-low temperature cooling water chiller. What is the reason?
1. The refrigeration system is not fully drained before charging refrigerant
Before the ultra-low temperature cooling water chiller is charged with the refrigerator, the compressor cylinder, condenser, evaporator and system pipeline in the refrigeration system have been filled with air. In order to eliminate these air before charging the refrigerant, it is necessary to vacuum the refrigeration system of the ultra-low temperature cooling water chiller. Sometimes, due to subjective and objective reasons, the vacuum in the refrigeration system is insufficient, If it fails to meet the requirements, a small amount of air is left inside the system.
2. Bring in when filling refrigerant
Before filling the refrigerant in the refrigeration system of the ultra-low temperature cooling water chiller, the pipes used for filling are filled with air. Due to human and other reasons, when filling the refrigerant, the air in the pipes is not exhausted, so they are directly connected to the refrigeration system, and these air enter the refrigeration system with the filled refrigerant.
3. Non condensable gas is mixed during maintenance of refrigeration system
When the refrigeration system of ultra-low temperature cooling water chiller works for a long time, it is inevitable to check, repair or clean and replace, so sometimes it is necessary to disassemble the machinery or pipeline, and the air often enters the refrigeration system in the process of disassembly and installation.
4. Chemical reaction from refrigerant
In the ammonia refrigeration system of ultra-low temperature cooling water chiller, refrigerant ammonia can be decomposed into ammonia and hydrogen at a certain temperature and pressure, and its decomposition degree has a positive relationship with temperature and pressure. The higher the temperature is, the greater the pressure is, the easier it is to decompose ammonia.
In the freon refrigeration system, freon may react with impurities mixed into the system to produce non condensable gas. For example, R12 reacts with water under certain conditions to produce carbon dioxide
5. The decomposition of lubricating oil will also produce non condensable gas
Among the lubricating oils used in the refrigeration system, some lubricating oils, such as mineral lubricating oil, can decompose under complex working conditions to produce a variety of hydrocarbon gases, which will be mixed into the refrigerant in the system.
These are the reasons for non condensable gas in the ultra-low temperature cooling water chiller. Users try to avoid these reasons in use and operate the ultra-low temperature cooling water system stably.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
December 5, 2022On November 18, 2022, it was sponsored by the Jiangsu Provincial Association for Science and Technology, the Provincial Taiwan Affairs Office, the Provincial Department of Industry and Information Tec...view
January 13, 2023Recently, the Jiangsu Provincial Productivity Promotion Center officially released the evaluation results of the unicorn enterprises and gazelle enterprises in 2022 in Jiangsu and the high-tech zone, ...view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view