The performance of the automatic temperature control system of the reactor is very important. Once you encounter a failure that cannot be started, you must solve it as soon as possible, oth...View details
High-power industrial refrigerators are used in industrial cold processing. Evaporators in high-power industrial refrigerators are one of the most important components and one of the factors affecting the cooling effect of high-power industrial refrigerators. Then, high-power industrial refrigerators are evaporated. What should I pay attention to during maintenance?
The evaporators in LNEYA high-power industrial refrigerators are generally well-matched in the design of high-power industrial refrigerators. In the case of high-power industrial refrigerators, high-power industrial refrigerator refrigeration systems can be better maintained to ensure efficient operation. Should pay attention to the influence of the liquid level on the evaporation temperature. Due to the influence of the height of the refrigerant liquid column of the high-power industrial refrigerator, the evaporation temperature at the bottom of the full-liquid evaporator is higher than the evaporation temperature of the liquid surface. Different refrigerants, high-power industrial refrigerators are subjected to hydrostatic liquid at different liquid surface evaporation temperatures. The effect of height is different. Regardless of which refrigerant is used, the lower the evaporation temperature of the liquid surface, the greater the effect of the hydrostatic height on the evaporation temperature. Therefore, the effect of the hydrostatic height on the evaporation temperature can be ignored only when the evaporation pressure is high.
The pressure loss of the high-power industrial refrigerator refrigerant in the evaporator is also an important factor. When the refrigerant flows through the evaporator, the pressure loss is caused, and the pressure p2 of the refrigerant at the outlet of the evaporator is inevitably lower than the pressure p1 at the inlet. , thereby reducing the suction pressure of the compressor, resulting in a decrease in refrigeration capacity. According to different high-power industrial refrigerator models, the evaporators of the unit are also different. For example, open high-power industrial refrigerators and screw-type high-power industrial refrigerators, shell-and-tube evaporators; box-type high-power industrial refrigerators. , is the use of water tank coil evaporator; acid and alkali high power industrial refrigerator, can choose titanium tube evaporator or stainless steel plate exchanger; a high-power industrial refrigerator, there are many options, of course, can be based on Customized by user needs.
Power industrial refrigerators require regular maintenance to extend the service life. Therefore, high-power industrial refrigerators need to pay attention to some details when using them to avoid some use failures.
The installation requirement of the industrial chiller: 1. Power supply (1) The chiller power supply adopts three-phase four-wire, power supply line (R, S, T) con...View details
The glass reactor is compact in volume and clear in structure, and can be conveniently operated in series and parallel in a flexible manner, fully satisfying various process occasions; the ...View details