There are several connection methods for industrial chillers, which are suitable for pipe connection under different conditions.
First, welding connection
Welding is the most important and widely used connection method in pipeline engineering. Welding connection is a direct and fixed connection between pipe sections; it is commonly used in large-diameter steel pipes, high-temperature and high-pressure pipes, overhead steel pipes, buried or laid in trenches, etc. . It has obvious advantages such as high strength and tightness of the interface, omission of fillers and joint accessories, fast construction speed, and no limitation of pipe diameter; but it also has the advantages of non-disassembly, complex interface operation technology, and welding equipment and welder cooperation during construction. And other shortcomings.
Second, threaded connection
Threaded connection (also called threaded connection), it is suitable for pipes with small working pressure and small nominal diameter (dn≤32mm), as well as the connection of pipes with threaded valves, instruments, and equipment. When connecting, the joint should be smeared with filler prepared by lead oxide and glycerin, and evenly spread on the thread of the pipe thread (do not apply in the valve), or use PTFE plastic tape as the filler. The filler shall not protrude into the pipe to avoid reducing the pipe. On the end face, it is strictly forbidden to replace the filler with white painted hemp wire, and the wire connection must be tightened once, and shall not be returned or loosened.
Third, flange connection
Flange connection is to add gaskets (materials) to a pair of flange plates fixed on two pipe fittings, and then tighten them with bolts to connect them into a detachable whole. It has high connection strength, good sealing performance, convenient disassembly, and standardization of production. Therefore, it is widely used in equipment connections between pipes and flanged pipe fittings or flange interfaces, pipes and flange valves, and pipes. The location that needs to be disassembled and overhauled. During installation, a rubber plate gasket with a thickness of 4mm should be placed in the notch. The gasket shall not have uneven thickness, bevel or notch.
We at LNEYA will make a specific analysis according to the customer’s specific working conditions. If you have equipment requirements or equipment problems, please contact us email@example.com
Laboratory ultra low temperature freezer is also called cryogenic storage box, cryogenic refrigerator, etc. Common - 40, - 60, - 86 degrees Celsius ultra low temperature freezers are suitable for cryogenic test of electronic devices and...View Details
Regular maintenance work for the material aging test chiller, and troubleshooting is also very important.1. Exhaust at double high pressure, heat dissipation may be problematic. When it is detected that the high and low pressure of the sys...View Details
Due to different compressors, the performance of low temperature chiller circulation machine is also different. Screw compressor is different from the piston compressor, whose structure is more sophisticated. Therefore, if the user needs t...View Details
Spot high and low temperature impact test chamber, also known as three-box high and low temperature impact test chamber, high and low temperature impact test chamber is mainly composed of low temperature storage chamber, high temperature s...View Details