How to deal with the frosting of the chiller?
There are many types of chillers, and customers familiar with this piece are definitely familiar with the chiller. For the frosting of the chiller, many people are ignorant, and then let's learn more about it with LNEYA!
1. If it is a chiller, please check if the opening degree of the expansion valve is too large. The small point can be fine-tuned (if it is an electronic expansion valve adjustable circuit control panel).
2. If the opening degree of the expansion valve is too small or blocked, the liquid supply of the refrigerant will decrease, which will cause the evaporation temperature to be low, causing frost on the fins of the evaporator; if the refrigerant does not flow back to the flow back Continued evaporation in the trachea and compressor will cause frosting of the compressor and return line.
3. Check if the filter is too dirty, or the evaporator fins are too dirty to make the heat exchange effect poor, and the refrigerant evaporation does not flow back to the return pipe and the compressor continues to evaporate, resulting in frost formation.
4. If the operating environment of the chiller is not good, or the air does not circulate, it will also cause the heat dissipation effect to affect the unit frost.
5. Check if the amount of refrigerant is within the standard range. Whether the filling is too much or too little will affect the normal operation of the chiller.
6. Is it the use of multiple chillers in parallel? If the number of units to be turned on is large, it is necessary to check whether the start time of the frosting unit is too long (the combined unit has a control panel to set the opening and closing time of each chiller as required).
For the failure of the chiller, LNEYA tells everyone that it is necessary to use professional knowledge to solve the problem in time, and check the equipment in time to avoid any malfunction.
- January 11, 2018The LNEYA Group will participate in the ACHEMA -World Forum and Leading Show for the Process Industries,Frankfurt am Main, Germany.view
- January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
- July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
- July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
- September 11, 2018Automotive Testing Expo 9.25-9.27view
- July 4, 2018Guanya is a leading role in heating cooling circulator. It provides the customers with proposal and technology of controlling the cold and heat, temperature control system with stable property, extend...view
- January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
- April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
- April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
- April 10, 2018Low Temperature Cooling Chiller LT model: LT-5018N，LT-5040N，LT-5062N，LT-5090N，LT-50A1N，LT-50A2N; Medium Temperature Range: -45℃～30℃. ASET multifunctional controller, control outlet temperature of water tankview
- February 28, 2019-45℃~+200℃
- February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view