How to replace the four-way valve of the chilled water machine?
The four-way valve of the chilled water machine needs to be replaced in time after a long period of use, so how to replace it? You can look at the suggestions.
When replacing the chilled water machine, you need to remove the connecting pipe connecting the compressor exhaust pipe and the suction pipe first. Because the pipes connecting the condenser and the three-way valve on the four-way room of the refrigerator are relatively close, it is not easy to get from the pipe port. Take it out, so the pipe connecting the compressor discharge pipe and suction pipe should be removed first.
Next, remove the connecting pipe connecting the three-way valve and the condenser, and use the torch of the chilled water machine to heat the four-way valve at the same time to connect the three-way valve and the condenser pipe interface. When the two nozzles are red and the solder starts to flow Use pliers to clamp the pipe connecting the four-way valve to the compressor exhaust pipe and lift it up. When the two pipe ports reach a certain temperature and the connecting pipe is loosened, the four-way valve can be removed.
The chiller needs to pay attention to the high temperature when welding the four-way valve nozzle, which will easily damage the plastic valve block in the valve body. Therefore, the valve body should be wrapped with a towel to cool down, and the temperature of the valve body is transmitted through the 3 pipes at the root. The 3 pipes at the root should be wrapped first. Since the pipe connecting the compressor exhaust pipe is far from the valve body of the four-way valve, the temperature will not damage the internal valve block during welding, so there is no need to wrap the nozzle with a towel.
When installing the four-way valve body, you can use a welding torch to heat the nozzles of the 3 pipes at the root of the four-way, so that the remaining solder on the surface is fully melted and flows until it falls off, so that the surface of the nozzle is smooth, so that it can be inserted into the four-way smoothly. Valve nozzle. Because the difficulty of welding lies in the three pipes at the root, the pipe connecting the compressor exhaust pipe can be pulled to one side, and after welding the three nozzles, weld the pipe connecting the compressor exhaust pipe.
Since it is difficult to weld the middle pipe between the four-way, the middle pipe should be welded first, then the pipes on both sides should be welded, and then the pipe connecting the compressor exhaust pipe should be welded. After the compressor exhaust pipe nozzle is installed and welded, the four joints are welded. La
After installing the four-way valve of the chiller, you need to pay attention to the leakage detection of the refrigeration system, and then put it into use after the leakage detection is completed.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
April 10, 2018Low Temperature Cooling Chiller LT model: LT-5018N，LT-5040N，LT-5062N，LT-5090N，LT-50A1N，LT-50A2N; Medium Temperature Range: -45℃～30℃. ASET multifunctional controller, control outlet temperature of water tankview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view