Routine maintenance points of special refrigeration units for laboratory instruments
Industrial refrigeration units dedicated to laboratory instruments are used more in the pharmaceutical and chemical industries, and care must be taken when using them.
The daily maintenance of the industrial refrigeration unit dedicated to experimental instruments is mainly reflected in the following aspects:
1. Condenser The high-temperature and high-pressure Freon of the refrigeration system of the industrial refrigeration unit dedicated to the experimental instrument comes out of the compressor and enters the condenser, releasing a large amount of heat to the cooling medium and being liquefied by the cooling. If the industrial refrigeration unit dedicated for laboratory instruments has been used for more than half a year, or the high and low pressure engines frequently fail, or the cooling capacity is reduced, please arrange a technician to clean the condenser. The fin condenser is generally cleaned with a high-pressure water gun. Be careful not to clean it sideways, which can easily cause the fin to fall over. Shell-and-tube condensers are generally immersed and circulated with descaling chemicals, and then the end cover is opened, and the pipes are cleaned one by one with a gun gun. Cleaning the condenser can significantly improve the refrigeration efficiency of the industrial refrigeration unit dedicated to laboratory instruments.
2. Compressor Every time the compressor operating time of the industrial refrigeration unit dedicated to the experimental instrument exceeds one thousand hours, all details of the compression equipment should be checked. For example: whether the lubricating oil is normal; whether the running current of the compressor is normal; whether there is any abnormality when the compressor is running. Of course, the current refrigeration technology is quite mature, there are many sensors and protectors. When the unit alarms the fault, it should be repaired according to the fault location. When the compressor makes abnormal noise when it is running, it should be shut down for maintenance, mostly due to insufficient lubricant.
3. Refrigerant The industrial refrigeration unit dedicated to experimental instruments is an indispensable equipment for industrial production now, and each unit is inseparable from the participation of refrigerant, so the lack of refrigerant will affect the normal operation of the machine and will appear The cooling capacity of the industrial refrigeration unit dedicated to the experimental instrument is insufficient, or the cooling temperature is very slow.
Routine maintenance cannot be ignored. Effective maintenance can keep the industrial refrigeration unit dedicated to laboratory instruments in an effective state of operation.
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
July 4, 2018Guanya is a leading role in heating cooling circulator. It provides the customers with proposal and technology of controlling the cold and heat, temperature control system with stable property, extend...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
April 10, 2018Low Temperature Cooling Chiller LT model: LT-5018N，LT-5040N，LT-5062N，LT-5090N，LT-50A1N，LT-50A2N; Medium Temperature Range: -45℃～30℃. ASET multifunctional controller, control outlet temperature of water tankview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view