Relationship Between Poor Refrigeration Performance And Refrigerant In Low Temperature Industrial
The effect of the refrigeration system of the low-temperature industrial refrigerator is directly related to the refrigerant. Once the refrigerant leaks, the cooling capacity will be insufficient, so that the suction and exhaust pressures are relatively low, and the expansion valve and the evaporator are in operation. The balance pressure cannot be maintained. Therefore, if the refrigerant leaks from the low-temperature industrial refrigerator (group) is found, it is not rushed to fill the system with the refrigerant. Instead, the leak point should be immediately found and the refrigerant should be filled after repair.
In the refrigeration system of the low-temperature industrial refrigerator (group), pay attention to the amount of refrigerant, too little, too much, too much, too much may cause the exhaust pressure of the low-temperature industrial refrigerator to rise, higher than the normal value, need to stop in time, use High pressure exhaust removes excess refrigerant from the system.
If the low-temperature industrial refrigerator (group) is filled with too much refrigerant after maintenance, the cooling effect will be worse, because the charge of the refrigerant will occupy a part of the condenser of the low-temperature industrial refrigerator (group), which is reduced. The cooling area and cooling efficiency are also decreasing, and the cooling rate is continuously decreasing. Therefore, according to the operation sequence, after the machine is shut down for a few minutes, excess refrigerant is released at the high pressure shut-off valve, and the residual air in the system can be released at the same time.
Of course, the refrigeration system inside the low-temperature industrial refrigerator (group) also needs to pay attention to, once the air in the low-temperature industrial freezer (group) refrigeration system will reduce the cooling efficiency, this time can be several times after a few minutes after the shutdown The high pressure shut-off valve releases air, and it is also possible to properly fill some refrigerant according to the actual situation.
The refrigeration effect of the low-temperature industrial refrigerator (group) is closely related to the amount of refrigerant. Therefore, users should pay attention to the refrigeration effect in time and strive for better operation of the low-temperature industrial refrigerator (group).
- January 11, 2018The LNEYA Group will participate in the ACHEMA -World Forum and Leading Show for the Process Industries,Frankfurt am Main, Germany.view
- January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
- July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
- July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
- September 11, 2018Automotive Testing Expo 9.25-9.27view
- July 4, 2018Guanya is a leading role in heating cooling circulator. It provides the customers with proposal and technology of controlling the cold and heat, temperature control system with stable property, extend...view
- January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
- April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
- April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
- April 10, 2018Low Temperature Cooling Chiller LT model: LT-5018N，LT-5040N，LT-5062N，LT-5090N，LT-50A1N，LT-50A2N; Medium Temperature Range: -45℃～30℃. ASET multifunctional controller, control outlet temperature of water tankview
- February 28, 2019-45℃~+200℃
- February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view