The reason for the high pressure alarm of the TCU integrated temperature control unit
When the TCU integrated temperature control unit is used, it needs to be used according to the instructions in detail. Once problems are encountered, they need to be dealt with in time. Generally speaking, if we encounter a high pressure alarm from the compressor, then we need to carefully analyze various reasons. The reasons include more refrigerant filling, poor condensation effect, electrical failure and many other reasons. So, how should it be handled?
1. There is a lot of refrigerant filling: the main manifestation is that the pressure of suction and exhaust and balancing is too high, and the pressure of the compressor operating current is too large. When in use, it is necessary to ensure its exhaust and balanced pressure according to the rated working conditions, and to ensure that the operating current discharges the refrigerant until the performance is normal.
2. The pipeline filter is blocked or too thin, and the water passing capacity is limited. A suitable filter should be selected and the filter screen should be cleaned regularly; or the pump should be small and not matched with the system.
4. False alarms caused by electrical faults, due to damp, poor contact or damage to the high-voltage protection relay, damp or damaged unit electronic boards, and false alarms caused by communication failures. For this kind of false fault, the fault indicator on the electronic board is often not bright or slightly bright, the manual reset of the high-voltage protection relay is invalid, the running current of the compressor is normal, and the suction and exhaust pressure is also normal.
5. At this time, the expansion valve should be gradually opened, and the opening process should not be too fast to prevent the copper tube in the evaporator from being damaged by too much liquid supply. Wait for a few minutes until the high and low pressure of the unit are balanced. At this time, a lot of white foam can be seen from the sight glass of the evaporator, which means that the oil has entered the evaporator from the condenser.
If the process temperature control unit you are using is the ZLF or SR series of our TCU, you can contact us if you have any questions.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
July 4, 2018The refrigeration system of cold plate freezer adopts secondary super-cooler technology with the rapid refrigeration and low limiting temperature. It uses imported brand name semi-hermetic piston comp...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view