Maintenance and maintenance of battery pack test temperature simulation chiller
The battery pack test temperature simulation chiller is more and more widely used in enterprises, but the subsequent maintenance and maintenance are also more important. Here is a brief introduction to some maintenance and maintenance methods.
1. The temperature of the battery pack that does not need to be opened is not closed before the start-up to simulate the water inlet valve of the condenser on the chiller, resulting in water leakage. Part of the cooling return water flows away from the condenser of the non-starting unit, reducing the cooling water flow in the condenser of the operating unit, causing the condensation pressure to rise, the operating current of the main engine to increase, and the cooling capacity of the unit to decrease. Stopping the operation not only wastes electricity, but also reduces the cooling effect, and is easy to damage the equipment.
2. Before starting up, close the water inlet valve of the condenser of the unit that does not need to be operated to prevent water leakage. Open the water inlet and outlet valves on the condenser of the unit to be operated (generally the outlet valve is normally open, the water inlet valve is opened and closed according to needs. The condenser and the evaporator are the same) and turn on the corresponding cooling water pump to adjust the water inlet and outlet pressure of the condenser.
3. If the pointer of the pressure gauge of the water inlet and outlet of the condenser swings too much, it means that there is air in the equipment system, and the air needs to be exhausted to continue to the next step after the pressure gauge indicates normal.
4. It adopts an intelligent main control board, and the LED display is stable and durable, with multiple settings and fault display functions; it is equipped with a water outlet pressure gauge, which is convenient for observing pressure and flow.
February 6, 2021If you need equipment to distill CBD, you need to scrutinize your choices, as the equipment can vary in its features and design. When you use equipment that produces a CBD distillate, you want to seek out a system made by a manufacturer that provides proven and reliable products. You should also work with a business that can train you on the use of the equipment you buy.view
December 5, 2022On November 18, 2022, it was sponsored by the Jiangsu Provincial Association for Science and Technology, the Provincial Taiwan Affairs Office, the Provincial Department of Industry and Information Tec...view
January 13, 2023Recently, the Jiangsu Provincial Productivity Promotion Center officially released the evaluation results of the unicorn enterprises and gazelle enterprises in 2022 in Jiangsu and the high-tech zone, ...view
January 11, 2018Industrial Chiller：Industrial Chiller varies from dynamic temp. Special Chiller：Special Chiller consist of Multi-reactor chiller (TCU).Environmental Chamber：The test object is connected to a testing adapter. Industrial Freezer：Industrial freezer consist oview
July 4, 2018What are the characteristics and functions of ultra low freezer: 1. Ultra low freezer can prevent the precision of machine equipment from being influenced by the change of oil temperature in the proce...view
January 11, 2018Temperature ranges from - 5 ~ - 150 ℃, can meet different temperature; Adopt environmental protection refrigerants; Famous brand semi-closed piston compressor, semi-closed bipolar piston compressor, semi-hermetic screw compressor, main brand are BOCK.view
April 10, 2018Working temperature range from -25℃to 200℃, other temperature range need to set to the widest temperature range(-50℃to 250℃)
Centralized control of 2~20 reactors, each reactor's and jacket temperature can be set independently. One system control multipleview
April 10, 2018A set of cooling heat exchanger, heat exchanger, through proportional adjusting valve control cold heat into the heat exchanger, then through the uniform medium input to the reactor jacketed to do heat exchange and temp. Control, system has inside expansiview
February 28, 2019Temperature control range：-85 ° C ~ 200 ° CPower range：2.5kW~25kWTemperature control accuracy：±0.3°CModelTES-8525WTES-8555WTES-85A10WTES-85A15WTES-85A25WTemp. Range-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃-85℃～200℃Heating P...view